The user equipment plugs into the LCDP's equipment (protected) side, and the LCDP's line (unprotected) side is connected to the incoming line. All 8 conductors are protected. The green ground wire must be bonded to the protected equipment power ground (third
wire, green wire safety ground). Do not add length to the ground wire, for it must be kept as short as possible. For proper grounding methods, refer to EDCO Technical Bulletin #1090 located in the back of the 1998 catalog.
If you have reached this page through a browser and do not have the "Comm-Omni Navigation Bar" at the top, please follow
Return to Comm-Omni Home Page
To speak to one of our consultants, please call us at 1-800-543-8790